DDK Ventilation Products Ltd.
Building Products Listing Program
- DDK Ventilation Products Ltd.
- Firestopping - Penetration Firestopping
- Coquitlam, BC
- April 18, 2019
- April 18, 2019
CAN/ULC S115 Standard Method of Fire Tests of Firestop Systems
ASTM E814 Standard Test Method for Fire Tests of Penetration Firestop Systems
Sheet metal In-Slab Ventilation Duct Systems
Design Listing Fitting Type Maximum Inlet Size (in2) Duct Height (in) Minimum Slab Thickness (in) Intumescent pad F, FH Rating (min) T, FTH Rating (min) B1121-1A Fire stopped Inlet boot 49 1-3/4 6 1 layer 120 90 Fire stopped Inlet boot 49 1-3/4 6-1/4 1 layer 120 120 Fire stopped Inlet boot 49 1-3/4 6 2 layers 120 120 Dual fire stopped inlet boot 98 1-3/4 6 2 layers 120 90 Fire stopped Inlet boot 49 1-3/4 8 2 layers 180 180 Fire stopped Inlet boot 49 1-3/4 8 None 180 120 Dual fire stopped inlet boot 98 2 7 2 layers 120 90 Fire stopped Inlet boot 49 2 7 2 layers 120 120
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI.
No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing.
Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to email@example.com. Please include the listing number in the request.