Artsy Contracting Co. Ltd.
Windows & Doors Listing Program
- Artsy Contracting Co. Ltd.
- Fire Door Frames
- Delta, BC
- June 2, 2020
- June 2, 2020
CAN/ULC-S104 Standard Method for Fire Tests of Door Assemblies
UL 10B Standard for Fire Tests of Door Assemblies
20 Minute Neutral Pressure Rated Fire Door Frames
20-MINUTE NEUTRAL PRESSURE RATED CATEGORY C WOOD FIRE DOOR FRAMES WITH CATEGORY G GASKET REQUIRED
Swing Type: Maimum Dimensions Width: Height: Single Swing 3’6” (1067 mm) 8’4” (2540 mm) Pairs / Double Egress Not Permitted
The above frames are Category C, composed of MDF.
Frames are required installed with a Category G gasket fire-rated for minimum 20 minutes with wood door frames for neutral and positive pressure applications.
Minimum Frame Depth: 4-3/4”
Maximum Frame Depth: Equivalent to wall thickness
Minimum Frame Leg Thickness: 1’’ (25 mm)
Minimum Rabbet for Door: 1-3/4″ (-1/16”)
Minimum Stop Height: 1/2″ (13 mm)
Minimum Stop Width: 1-1/2’’ (38 mm)
Casing Thickness: 1/2’’ (13 mm)
Casing Width: 2’’ (51 mm)
Hardwood Facings: Permitted.
Electric Raceway: Not permitted.
Door Closers: Surface mounted: Permitted.
Mortised: Not permitted.
• Fastened through the frame legs with #8 x 3” (76 mm) length screws, at shim locations.
• 4 shims along each jamb, 1 shim at the header.
• Hinge and latch locations each use two #12 x 3-1/2” (89 mm) screws.
• Gaps are required to be sealed with silicone sealant prior to placement of casing.
• Casing to be anchored with finishing nails at minimum 18’’ on center spacing.
Refer to QAI evaluation report F445-2 and the applicable test reports for test assembly configurations used for fire endurance testing.
Refer to the QAI FD002 – Fire Door Guidelines for general guidelines of fire door assemblies
Final acceptance of the product in the intended application is to be determined by the authority having jurisdiction (AHJ).
Product is to be installed in accordance with the manufacturer’s published installation instructions by qualified installing personnel.
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI.
No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing.
Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to email@example.com. Please include the listing number in the request.