Ecco Doors Manufacturing LLC
Windows & Doors Listing Program
- Ecco Doors Manufacturing LLC
- Fire Resistant Doors
- Boynton Beach, FL
- December 11, 2019
- December 11, 2019
CAN/ULC S104 Standard Method for Fire Tests of Door Assemblies
UL 10B Fire Tests of Door Assemblies
UL 10C Positive Pressure Fire Tests of Door Assemblies
NFPA 252 Standard Methods of Fire Tests of Door Assemblies
UBC-7-2 (1994) Uniform Building Code
UBC-7-2 (1997) Uniform Building Code
ASTM E2074 Standard Test Method for Fire Tests of Door Assemblies, Including Positive Pressure Testing of Side-Hinged and Pivoted Swinging Door Assemblies
20 minute Neutral and Positive Pressure Rated Category “B” Fire Doors
with Hose Stream.
20 MINUTE CR ROUTED FLUSH AND FUSION PANEL DOORS:
Swing Type Maximum Dimensions Panel Type Latching Width Length Single Swing 4’0”
Routed Flush Single Point
(Mortised or Cylindrical)
Flat or Raised Panel Pairs 8’0”
Routed Flush 3 or 4 point
(Active: Mortised or Cylindrical)
[Manual or Automatic]
and Surface Mounted Bolts)
Flat or Raised Panel Double Egress Not Permitted
Limitations: (Review Machining Report for further detail)
• Cylindrical Latches (Listed and Labeled)
• Multi-Point Latch (Listed and Labeled)
• Deadbolts (Listed and Labeled)
• Fire Exit Devices (Listed and Labeled)
o Surface mounted vertical rod, and RIM exit devices
• Surface Mounted Door Closer (Listed and Labeled)
• Light Kit (Listed and Labeled)
o Listed Steel Lite Kit – max. 1296 sq. in. (max dimension of 54”)
• Mortise Manual or Automatic Flushbolts (Listed and Labeled)
• Surface Mounted Protection Plates
o Maximum 12” high
• Viewers (Listed and Labeled)
o Maximum size of 1” diameter located a minimum 5-1/2” away from door edges
o Multiple viewers located a minimum of 12” on center
• Surface Mounted Door Bottom (Listed and Labeled)
o Max mortise 1-3/4” deep by 1” wide by full width of the door
Refer to QAI evaluation report F463-1 and the applicable test reports for test assembly configurations used for fire endurance testing.
Refer to the QAI FD002 – Fire Door Guidelines for general guidelines of fire door assemblies
Final acceptance of the product in the intended application is to be determined by the authority having jurisdiction (AHJ).
Product is to be installed in accordance with the manufacturer’s published installation instructions by qualified installing personnel.
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI.
No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing.
Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to firstname.lastname@example.org. Please include the listing number in the request.