Metl-Span, A Division of NCI Group, Inc.
Building Products Listing Program
- Metl-Span, A Division of NCI Group, Inc.
- Insulated Metal Wall Panels
- 1720 Lakepointe Drive, Lewisville, Texas
- October 15, 2015
- April 7, 2020
CAN/ULC S138 “Standard Method of Test for Fire Growth of Insulated Building Panels in a Full-scale Room Configuration”.
CAN/ULC S102 “Standard Method of Test for Surface Burning Characteristics of building Materials and Assemblies”.
Metl-Span CleanSeam™ Wall and Ceiling Panels.
Metl-Span CleanSeam™ Joint Sealant
(FRP joint sealing material)
CleanSeam™ panels are marked with labels supplied by Metl-Span. The label includes:
• Manufacturer’s Name,
• Manufacturing Address,
• Product Name,
• Class A Flame Spread,
• QAI Logo with “C” and “US” indicator, and
• QAI Listing Number (B1087).
Note Metl-Span CleanSeam™ Wall and Ceiling Panels are also certified to US requirements see US Listing
The following outlines Metl-Span CleanSeam™ Wall and Ceiling Panels with CleanSeam™ Joint Sealant connections performance determined in accordance with the noted standards.
Metl-Span CleanSeam™ Wall and Ceiling Panels with Sealant CAN/ULC S102 and CAN/ULC S138 Results:
QAI Design # Flame Spread Index Smoke Developed Index Max. Panel Thickness CAN/ULC-S138 B1087-1b2 ≤ 25 ≤ 250 152 mm
Sprinklered Room Compliant when installed with Listed Pendant Style Sprinkler with 68oC (155oF) Activation Temperature
Note 2: The above assembly has been evaluated and found compliant for Protection of
Foam Plastic in Combustible Construction as outlined in Section 188.8.131.52 of the 2015
National Building Code of Canada (NBC).
The above assembly has been evaluated and found compliant for Factory Assembled
Panels for use in Non-Combustible Construction for buildings that are sprinklered, < 18 meters high, have no Group A Group B or Group C major occupancies, with the panel having no air spaces, as outlined in Section 184.108.40.206 of the 2015 NBC and where panels are
used in application where flame spread ratings required are ≤ 25.
This assembly is not evaluated for fire-resistance rated wall applications.
Final acceptance of the product in the intended application is to be determined by the authority having jurisdiction.
Product is to be installed in accordance with the QAI Design Listing and manufacturer’s published installation instructions by qualified installing personnel.
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI. No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing. Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to firstname.lastname@example.org. Please include the listing number in the request.