Zurn Pex, Inc
Plumbing Listing Program
- Zurn Pex, Inc
- Pex Piping System
- Commerce, TX
- September 24, 2014
- January 31, 2020
ASTM E84 “Standard Test Method for Surface Burning Characteristics of Building Materials”
CAN/ULC S102.2 “Standard Method of Test for Surface Burning Characteristics of building Materials and Assemblies”
Pex Piping System
The finished product bears the following information: Product Name, Product nominal size, Manufacturer name, City and state of manufacture, QAI Logo with the “us” indicator, QAI file number, Date of manufacture, the standard “ASTM E84”, Flame Spread Rating < 25, Smoke Developed Rating < 50, and the wording “must be installed with Zurn ZPEX Pipe Support or rated ½-inch pipe insulation as described in QAI Listing”.
Zurn Cross-linked polyethylene (PEX) pipe (red, white and blue colors) installed with either Zurn ZPEX Pipe Supports or rated ½-inch pipe insulation.
Characteristics per ASTM E84:
Products Limitations Flame Spread Index Smoke Developed Index Q8PS20X (2”) Q7PS20X (1-1/2”) Q6PS20X (1-1/4”) Q5PS20X (1”), XL Fittings and ZPEX Supports Maximum 2-inch nominal diameter piping, supported continuously with 23 gauge Zurn ZPEX Pipe Supports, with any (joint) gap distance between ZPEX supports covered by an approved pipe insulation1. Maximum 2 adjacent Zurn PEX pipe runs per plenum / cavity. < 25 < 50 Q8PS20X (2”) Q7PS20X (1-1/2”) Q6PS20X (1-1/4”) Q5PS20X (1”), XL Fittings and ZPEX Supports
Maximum 2-inch nominal diameter piping, installed with rated ½-inch pipe insulation1; No spacing requirements between adjacent runs. Optionally can be installed with Zurn ZPEX Pipe Supports.
< 25 < 50 Q3PS20X (1/2”), Q4PS20X (3/4”), XL Fittings and ZPEX Supports Maximum ¾-inch nominal diameter tubing installed bare. Optional rated ½-inch pipe insulation or with Zurn ZPEX supports can be used. Minimum 18-inch on center spacing between adjacent pipe runs. <25 <50 Note1: List of approved pipe insulation providers in the Insulation table at the end of the listing.
Zurn Pex piping described below have the following Surface Burning Characteristics per CAN/ULC S102.2.
Products Limitations Flame Spread Index Smoke Developed Index Q3PS20X (1/2”) Maximum 1/2-inch nominal diameter tubing. No spacing requirements per adjacent runs. < 25 < 50
The following list of pipe insulation types (at minimum thickness of ½”) are approved for use with Zurn PEX piping at a maximum nominal diameter of 2”. The insulations noted when Listed to ASTM C547 by an approved agency, are approved for use at the dimension specified above.
Insulation Flame Spread Rating (according to ASTM E84) Smoke Developed Rating (according to ASTM E84) Mason Alley-K < 25 < 50 Armaflex Composite < 25 < 50 Johns Manville Micro-Lok < 25 < 50 Johns Manville Micro-Lok HP < 25 < 50 Owens Corning Vapor Wick < 25 < 50 Owens Corning Fiberglass < 25 < 50 GLT Pipe and Tank < 25 < 50 Knauf Earthwool Redi-Klad < 25 < 50 Nomalock < 25 < 50
The product must be installed in accordance with the code enforced by the authority having jurisdiction. Final acceptance of the product in the final installation is subject to inspection by the authority having jurisdiction.
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI.
No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing.
Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to email@example.com. Please include the listing number in the request.