LOGIX Insulated Concrete Forms, Ltd.
Building Products Listing Program
- LOGIX Insulated Concrete Forms, Ltd.
- Insulated Concrete Forms (ICF)
- Vancouver, BC
- September 27, 2010
- August 24, 2015
ASTM E2634 “Standard Specification for Flat Wall Insulating Concrete Form (ICF) Systems”.
ASTM D635 “Standard Test Method for Rate of Burning and/or Extent and Time of Burning of Plastics in a Horizontal Position”.
ASTM D1929 “Standard Test Method for Determining Ignition Temperature of Plastics” ASTM D1761 “Standard Test Methods for Mechanical Fasteners in Wood”.
CAN/ULC S717.1 “Standard for Flat Wall Insulating Concrete Form (ICF) Systems”.
CAN/ULC S701 “Thermal Insulation, Polystyrene, Boards and Pipe Covering”.
CAN/ULC S102.2 “Standard Method of Test for Surface Burning Characteristics of Flooring, Floor Coverings, and Miscellaneous Materials and Assemblies”.
ASTM C578 “Standard Specification for Rigid, Cellular Polystyrene Thermal Insulation”.
ASTM E84 – “Standard Test Method for Surface Burning Characteristics of Building Materials”.
UBC 26-3 “Room Fire Test Standard For Interior of Foam Plastic Systems”.
CAN/ULC S101 “Standard Methods of Fire Endurance Tests of Building Construction and Materials”.
ASTM E119 / ANSI / UL 263 “Standard Test Methods for Fire Tests of Building Construction and Materials”.
LOGIX Insulated Concrete Forms (ICF)
- Product is marked with labels supplied by LOGIX Insulated Concrete Forms, Ltd. The label includes the manufacturer’s name, trademark, or other recognized symbol of identification, the product model designation, month and year of manufacture or equivalent, QAI logo with the ‘US’ and “C” identifier, and CAN/ULC S701 Type 2, ASTM C578 Type II, ASTM E84 FSI and SDI Rating, and CAN/ULC S102.2 FSI and SDI Rating. Labels are applied to palletized finished products to ensure visibility on the jobsite.
LOGIX Insulated Concrete Forms are Type II expanded polystyrene of nominal 1.5 lbs/ft3 density, complying with ASTM E2634 for use as flat walled insulating concrete forms. LOGIX ICF cross ties are minimum CC2 classification per ASTM D635, with a spontaneous ignition temperature of greater than 650oF per ASTM D1929. The following outlines LOGIX ICF test results determined in accordance with the noted standards. LOGIX ICF Fastener Resistance Ratings per ASTM D1761.
FASTENER ALLOWABLE WITHDRAWAL ALLOWABLE LATERAL SHEAR lbs kg lbs kg #6 1 ¼ inch Length Coarse Thread Drywall Screw 23 10 59 26
LOGIX ICF Type 2 Specifications per CAN/ULC S701
PROPERTY LOGIX SPECIFICATION Thermal Resistance m2*oC/W at 25 mm Thickness Minimum 0.70 Water Vapour Permeance Ng/Pa*s*m2 at 25 mm Thickness Maximum 200 Dimensional Stability % Linear Change Maximum 1.5 Flexural Strength kPa Minimum 240 Water Absorption % Volume Maximum 4.0 Compressive Strength kPa at 10% Deformation Minimum 110 Limiting Oxygen Index % Minimum 24
LOGIX ICF Type II Specifications per ASTM C578
PROPERTY LOGIX SPECIFICATION Compressive Resistance psi at Yield or 10% Deformation Minimum 15.0 Thermal Resistance F*ft2*h/Btu at 1.00 Inch Thickness Minimum 4.0 Flexural Strength psi Minimum 35.0 Water Vapor Permeance Perms at 1.00 Inch Thickness Maximum 3.5 Water Absorption % Volume Maximum 3.0 Dimensional Stability % Change Dimensions Maximum 2.0 Oxygen Index % Volume Minimum 24.0 Density lbs/ft3 Minimum 1.35
LOGIX ICF Surface Burning Characteristics per CAN/ULC S102.2
LOGIX COMPONENT DENSITY MAXIMUM THICKNESS FLAME SPREAD INDEX (FSI) SMOKE DEVELOPED INDEX (SDI) Expanded Polystyrene (EPS Panel) 22 – 29 kg/m3 100 mm Maximum ≤ 210 ≥ 500
LOGIX ICF Surface Burning Characteristics per ASTM E841
LOGIX COMPONENT DENSITY MAXIMUM THICKNESS FLAME SPREAD INDEX (FSI) SMOKE DEVELOPED INDEX (SDI) Expanded Polystyrene (EPS Panel) 1.35 – 1.80 lbs/ft3 4.0 Inches Maximum ≤ 75 ≤ 450
1Ceiling Measurement Only. This measurement is conducted through determination of flame spread index and smoke developed index with the removal of any contribution of molten materials ignited on the floor of the tunnel assembly. LOGIX UBC 26-3 Configuration Meets requirements with ½ inch thickness gypsum fastened with 2 ¼ inch length standard drywall screws at 12 inch on center. Fasteners must be anchored into LOGIX ICF web ties.
Final acceptance of the product in the intended application is to be determined by the authority having jurisdiction.
Product is to be installed in accordance with the manufacturer’s published installation instructions by qualified installing personnel.
The materials, products or systems listed in this directory have been qualified to bear the QAI Listing Mark under the conditions stated with each Listing. Only those products bearing the QAI Listing Mark are considered to be listed by QAI. No warrantee is expressed or implied, and no guarantee is provided that any jurisdictional authority will accept the Listing found herein. The appropriate authorities should be contacted regarding the acceptability of any given Listing. Visit the QAI Online Listing Directory located at www.qai.org for the most up to date version of this Listing and to validate that this QAI Listing is active. Questions regarding this listing may be directed to email@example.com. Please include the listing number in the request.